Liebert Series Uninterruptible Power System (UPS) for the Single Module The Series UPS has been designed for Commercial/Industrial use only. Single Phase UPS system S i n g l e m o d u l e a n d ‘1 + N’ (e x p a n d a b l e) UNINTERRUPTIBLEPOWERSYSTEM User Manual EMERSON Network Power. Single phase ups system • Read online or download PDF • Emerson User Manual.
|Published (Last):||13 November 2014|
|PDF File Size:||6.53 Mb|
|ePub File Size:||5.74 Mb|
|Price:||Free* [*Free Regsitration Required]|
An upgrading kit s.
Further internal safety screens make the equipment protected to IP20 standards. Post ads for free Login Register How to partner with Clasf. Isolate the UPS input mains supply externally also the bypass supply if a split bypass is in use and isolate the eemrson. Both the connectors are with screwed terminals. If emersln is your first Liebert UPS, we hope it is e,erson beginning of a long relationship which delivers value to your organisation.
To provide a clean no-break load transfer between the inverter output and static bypass line, the inverter output and bypass supply must be fully synchronised during normal operating conditions. ENP is not responsible for supply of these interconnection cables in case the recommended Line up is altered. During normal operation both the rectifier and inverter sections are active and provides regulated load power whilst simultaneously float charging the battery.
Visit our blog Share on Facebook Share on Twitter. Input isolator is closed. This should be completed before you touch any switch.
This box is designed to be wall mounted and is connected between the UPS and battery bank. Such installations may utilise nonsealed lead acid cells, requiring regular attention and impose their own environmental requirements.
Study the connection diagrams in figures It is presumed that a b c d All the panels are in single line up. Location of UPS panels remain unchanged. Cable fixing samples from method 1 3. The risk of contact with these voltages is minimised as the live component parts are housed behind a hinged, lockable door. In a Non-Redundant module system both modules must be running before the load is transferred to their paralleled inverters.
Gain full access to the UPS interior by opening its internal hinged safety panel. Carry out a thorough examination of the UPS power components and sub-assemblies, paying particular attention to the following Electrolytic capacitors – Check for signs of leakage, buckling etc.
If you are unsure as to how to undertake the actions detailed – or if several LED indications are abnormal and you are unable to distinguish between the likely cause and affects – then seek immediate assistance from an approved service agent.
Note that LS5 will extinguish when LS6 illuminates. Measure and record the UPS output voltage on all three phases. These can be removed once the equipment has been finally positioned. Its purpose it to enable the critical load to be powered from the mains bypass supply while the UPS is shut down for maintenance or troubleshooting.
Connect the UPS bypass supply cables between the bypass distribution panel and the UPS bypass supply terminals on each module. The cut out dimensions for the panel mounting, are as shown in the clamps provided for wall mounting are required to be removed.
Connect one ribbon cable between sockets CN1 on one board and CN2 on emmerson other, and connect the second ribbon cable between the remaining CN1 and CN2 sockets. Open the Output Isolator on both modules.
If you encounter any problem with the procedures contained in this manual you should seek immediate assistance from Emerson Network Power Ejerson Pvt.
When using the above contacts for remote alarm annuciation, the power supply for the remote indicators must be provided from an external power source. Click for more information: Input filter In addition to these options, it is possible for the customer to use an RS extension of the operator control panel fitted as standard emersno external indications. Please do give us feedback to help us realise our Mission.
This facility is valid only for single module.
Bypass AC Input supply present: Inverter will not turn ON configuration at this stage. Reconnect the UPS input mains power. Connecting the emwrson interface cables.
However, it is important to maintain a regular record of the UPS meter emereon, as suggested in the maintenance instructions, in order that any change in the system or load characteristics are readily identified. A battery can present a risk of electric shock or burn from high short circus currents. This chapter contains information regarding the positioning and cabling of the one-plus-one UPS equipment and batteries. Certain procedures entail gaining internal access to the UPS, and should only be undertaken by a competent engineer who is familiar with the operation and layout of the equipment and understands the areas of potential hazard.
If a problem cannot be resolved by taking the actions given then fully trained assistance should emersno sought immediately.
UPS using the most direct route possible Emerson Network Power offer a purpose-designed emerxon battery circuit breaker box, containing the circuit breaker and its necessary control board, as a standard option emerspn. Once such a generator has been brought on-line, and the UPS input power has been re-established, the batteries immediately begin to recharge.
Min — Max — Voltage limits of Inverter operation for V d. If you already own and use a Liebert, we are doubly honoured by your decision of continuing this relationship.